It Begins Here
H2M’S Approach to Emerging Contaminants
A Conversation with the New York State Drinking Water Council
Piloting Our Way to the Future
Thinking Inside the Box
Where Do We Go From Here?
The Pilot Studies
H2M tested various Advanced Oxidation Process (AOP) treatment technologies across an array of groundwaters throughout Long Island, New York as part of our pilot program in anticipation of impending regulation schedule. H2M studied four different AOP technologies in their capacity to treat 1,4-dioxane and settled on one technology that was feasible for Long Island groundwater – Low Pressure UV light utilizing hydrogen peroxide oxidant (LP UV/H2O2).
At the conclusion of this study, H2M determined the specific water qualities that impact AOP treatment and deployed these four treatment technologies in time to meet a new imposed drinking water standard for 1,4-dioxane.
Rapid Deployment of AOP Wellhead Treatment
With no EPA Maximum Contaminant Level (MCL) set, New York State announced in 2017, it would establish contaminant specific MCLs in the State for 1,4-dioxane (and other perfluorinated compounds). The Governor’s office created a Drinking Water Council (DWQC) comprised of experts and stakeholders from across the State, to evaluate issues and offer recommendations to the NYSDOH. In December 2018, the DWQC recommended an MCL of 1.0 micrograms per liter (Mg/L) for 1,4-dioxane and 10.0 nano grams per liter (ng/L) each for PFOA and PFOS.
With no clear timeline provided for implementation of the new MCL, water purveyors were faced with making critical timing decisions in the context of operational impacts to their specific systems. Faced with a compressed schedule before the MCL became effective, and nearly two dozen emergency treatment systems needed in over 12-18 months, it was apparent that a typical design/construction plan would not work. Some water suppliers with wells that exceeded MCLs risked losing the ability to meet their peak demands. Others faced being forced to remove the majority of their wells from service, potentially risking the ability to provide even average daily demand requirements.
H2M derived and innovative and effective solution by creating an AOP “box” system. Working with our clients, vendors, and contractors, H2M developed a design and construction approach for an AOP treatment that condensed construction period from 18 months to six months.